## Heat Transfer Coefficient for Water in Tube Side in Shell and Tube Heat Exchanger Solution

STEP 0: Pre-Calculation Summary
Formula Used
Tube Side Heat Transfer Coefficient = 4200*(1.35+0.02*(Water Temperature))*(Fluid Velocity^0.8)/(Tube Inner Diameter)^0.2
hi = 4200*(1.35+0.02*(tw))*(Vf^0.8)/(di)^0.2
This formula uses 4 Variables
Variables Used
Tube Side Heat Transfer Coefficient - (Measured in Watt per Square Meter per Celcius) - Tube Side Heat Transfer Coefficient is the heat transfer coefficient for the fluid allocated in the tube side in shell and tube heat exchanger.
Water Temperature - (Measured in Celsius) - Water Temperature is the bulk temperature of water that is allocated on tube side of shell and tube heat exchanger.
Fluid Velocity - (Measured in Meter per Second) - Fluid Velocity is defined as the speed with which it flows over a surface.
Tube Inner Diameter - (Measured in Millimeter) - Tube Inner Diameter is the inside diameter of the tube where the fluid flow takes place.
STEP 1: Convert Input(s) to Base Unit
Water Temperature: 55 Celsius --> 55 Celsius No Conversion Required
Fluid Velocity: 2.5 Meter per Second --> 2.5 Meter per Second No Conversion Required
Tube Inner Diameter: 15.5 Millimeter --> 15.5 Millimeter No Conversion Required
STEP 2: Evaluate Formula
Substituting Input Values in Formula
hi = 4200*(1.35+0.02*(tw))*(Vf^0.8)/(di)^0.2 --> 4200*(1.35+0.02*(55))*(2.5^0.8)/(15.5)^0.2
Evaluating ... ...
hi = 12379.4412203118
STEP 3: Convert Result to Output's Unit
12379.4412203118 Watt per Square Meter per Kelvin -->12379.4412203118 Watt per Square Meter per Celcius (Check conversion here)
12379.4412203118 12379.44 Watt per Square Meter per Celcius <-- Tube Side Heat Transfer Coefficient
(Calculation completed in 00.004 seconds)
You are here -
Home »

## Credits

Malviya National Institute Of Technology (MNIT JAIPUR ), JAIPUR
Rishi Vadodaria has created this Calculator and 25+ more calculators!
Verified by Heet
Thadomal Shahani Engineering College (Tsec), Mumbai
Heet has verified this Calculator and 10 more calculators!

## < 5 Heat Transfer Coefficient in Heat Exchangers Calculators

Heat Transfer Coefficient for Subcooling Outside Horizontal Tubes
Subcooling Coefficient = 116*((Thermal Conductivity^3)*(Fluid Density/Pipe Outer Diameter)*(Specific Heat Capacity/Fluid Viscosity at BulThermal Conductivity Temperature)*Thermal Expansion Coefficient for Fluid*(Film Temperature-BulThermal Conductivity Fluid Temperature))^0.25
Heat Transfer Coefficient for Condensation Outside Vertical Tubes
Average Condensation Coefficient = 0.926*Thermal Conductivity*((Fluid Density/Fluid Viscosity at BulThermal Conductivity Temperature)*(Fluid Density-Vapor Density)*[g]*(pi*Pipe Outer Diameter*Number of Tubes/Mass Flowrate))^(1/3)
Heat Transfer Coefficient for Condensation Inside Vertical Tubes
Average Condensation Coefficient = 0.926*Thermal Conductivity*((Fluid Density/Fluid Viscosity at BulThermal Conductivity Temperature)*(Fluid Density-Vapor Density)*[g]*(pi*Pipe Inner Diameter*Number of Tubes/Mass Flowrate))^(1/3)
Heat Transfer Coefficient for Plate Heat Exchanger
Plate Film Coefficient = 0.26*(Thermal Conductivity/Equivalent Diameter)*(Reynold Number^0.65)*(Prandlt Number^0.4)*((Fluid Viscosity at BulThermal Conductivity Temperature/Fluid Viscosity at Wall Temperature)^0.14)
Heat Transfer Coefficient for Water in Tube Side in Shell and Tube Heat Exchanger
Tube Side Heat Transfer Coefficient = 4200*(1.35+0.02*(Water Temperature))*(Fluid Velocity^0.8)/(Tube Inner Diameter)^0.2

## Heat Transfer Coefficient for Water in Tube Side in Shell and Tube Heat Exchanger Formula

Tube Side Heat Transfer Coefficient = 4200*(1.35+0.02*(Water Temperature))*(Fluid Velocity^0.8)/(Tube Inner Diameter)^0.2
hi = 4200*(1.35+0.02*(tw))*(Vf^0.8)/(di)^0.2

## What is Shell and Tube heat exchanger?

A Shell and Tube Heat Exchanger is a type of heat exchanger widely used in various industrial processes to transfer heat between two fluids. It consists of a shell (a cylindrical vessel) and multiple tubes inside it. The two fluids flow in opposite directions, with one flowing inside the tubes (the tube-side fluid) and the other flowing outside the tubes but inside the shell (the shell-side fluid). Heat is exchanged between these two fluids through the tube walls.

## What is the Significance of Tube Side Heat Transfer Coefficient?

Tube Side Heat Transfer Coefficient quantifies how effectively heat is exchanged between the fluid inside the tubes (tube-side fluid) and the fluid outside the tubes (shell-side fluid) in a Heat Exchanger. Tube Side Heat Transfer Coefficient depends on parameters such as Reynolds Number, Prandlt Number and Thermal Conductivity of Tube Side Fluid.

## How to Calculate Heat Transfer Coefficient for Water in Tube Side in Shell and Tube Heat Exchanger?

Heat Transfer Coefficient for Water in Tube Side in Shell and Tube Heat Exchanger calculator uses Tube Side Heat Transfer Coefficient = 4200*(1.35+0.02*(Water Temperature))*(Fluid Velocity^0.8)/(Tube Inner Diameter)^0.2 to calculate the Tube Side Heat Transfer Coefficient, The Heat Transfer Coefficient for Water in Tube Side in Shell and Tube Heat Exchanger formula is a measure of how effectively heat is transferred from the water inside the tubes to the surrounding fluid or medium, typically in watts per square meter per degree Celsius (W/m²·°C). It quantifies the rate of heat transfer and is essential for designing and optimizing heat exchanger systems. Tube Side Heat Transfer Coefficient is denoted by hi symbol.

How to calculate Heat Transfer Coefficient for Water in Tube Side in Shell and Tube Heat Exchanger using this online calculator? To use this online calculator for Heat Transfer Coefficient for Water in Tube Side in Shell and Tube Heat Exchanger, enter Water Temperature (tw), Fluid Velocity (Vf) & Tube Inner Diameter (di) and hit the calculate button. Here is how the Heat Transfer Coefficient for Water in Tube Side in Shell and Tube Heat Exchanger calculation can be explained with given input values -> 12301.08 = 4200*(1.35+0.02*(328.15))*(2.5^0.8)/(0.0155)^0.2.

### FAQ

What is Heat Transfer Coefficient for Water in Tube Side in Shell and Tube Heat Exchanger?
The Heat Transfer Coefficient for Water in Tube Side in Shell and Tube Heat Exchanger formula is a measure of how effectively heat is transferred from the water inside the tubes to the surrounding fluid or medium, typically in watts per square meter per degree Celsius (W/m²·°C). It quantifies the rate of heat transfer and is essential for designing and optimizing heat exchanger systems and is represented as hi = 4200*(1.35+0.02*(tw))*(Vf^0.8)/(di)^0.2 or Tube Side Heat Transfer Coefficient = 4200*(1.35+0.02*(Water Temperature))*(Fluid Velocity^0.8)/(Tube Inner Diameter)^0.2. Water Temperature is the bulk temperature of water that is allocated on tube side of shell and tube heat exchanger, Fluid Velocity is defined as the speed with which it flows over a surface & Tube Inner Diameter is the inside diameter of the tube where the fluid flow takes place.
How to calculate Heat Transfer Coefficient for Water in Tube Side in Shell and Tube Heat Exchanger?
The Heat Transfer Coefficient for Water in Tube Side in Shell and Tube Heat Exchanger formula is a measure of how effectively heat is transferred from the water inside the tubes to the surrounding fluid or medium, typically in watts per square meter per degree Celsius (W/m²·°C). It quantifies the rate of heat transfer and is essential for designing and optimizing heat exchanger systems is calculated using Tube Side Heat Transfer Coefficient = 4200*(1.35+0.02*(Water Temperature))*(Fluid Velocity^0.8)/(Tube Inner Diameter)^0.2. To calculate Heat Transfer Coefficient for Water in Tube Side in Shell and Tube Heat Exchanger, you need Water Temperature (tw), Fluid Velocity (Vf) & Tube Inner Diameter (di). With our tool, you need to enter the respective value for Water Temperature, Fluid Velocity & Tube Inner Diameter and hit the calculate button. You can also select the units (if any) for Input(s) and the Output as well. Let Others Know